Our inspectors never know what a day might bring. One inspector sent these photos taken on the job.
A typical air tank suffering from being outside in a cement plant all the time.
This shows what a failed chemical injection pipe can do to a LWCO when the chemical spillage eats through the gaskets of the LWCO electrical box. As a result, it shorts the system and shuts off the feed water pump causing low water.
Our inspectors see a variety of issues in the field. This is an example of the internals of an LWCO electrical box damaged by chemical intrusion via a chem injection line.